We recently installed the EL040 Current monitoring kit with a TA011 clamp in our server room to monitor the current coming in to the Distribution Board from the UPS.
We get a reading of 246.1 Amp on Enviromon, but there's absolutely no way that the servers is drawing that much current, since the breaker in the Distribution Board is only 62 Amp breaker & it's not tripping.
Is the reading we're getting wrong? or do we need to convert the reading somehow to get the correct reading?
2 posts • Page 1 of 1